46 CFR 27.203 - What are the requirements for fire detection on towing vessels?
|Updated to:||October 2013|
Title 46: ShippingCHAPTER I: COAST GUARD, DEPARTMENT OF HOMELAND SECURITY SUBCHAPTER C: UNINSPECTED VESSELS PART 27: TOWING VESSELS Subpart B: Fire-Protection Measures for Towing Vessels 27.203 - What are the requirements for fire detection on towing vessels You must have a fire-detection system installed on your vessel to detect engine-room fires. Any owner of a vessel whose construction was contracted for before January 18, 2000, may use an existing engine-room-monitoring system (with fire-detection capability) instead of a fire-detection system, if the monitoring system is operable and complies with this section. You must ensure that? (a) Each detector, each control panel, and each fire alarm are approved under 46 CFR subpart 161.002 or listed by an independent testing laboratory; except that, if you use an existing engine-room-monitoring system (with fire-detection capability), each detector must be listed by an independent testing laboratory; (b) The system is installed, tested, and maintained in line with the manufacturer's design manual; (c) The system is arranged and installed so a fire in the engine room automatically sets off alarms on a control panel at the operating station; (d) The control panel includes? (1) A power-available light; (2) Both an audible alarm to notify crew at the operating station of fire and visible alarms to identify the zone or zones of origin of the fire; (3) A means to silence the audible alarm while maintaining indication by the visible alarms; (4) A circuit-fault detector test-switch; and (5) Labels for all switches and indicator lights, identifying their functions; (e) The system draws power from two sources, switchover from the primary source to the secondary source being either manual or automatic; (f) The system serves no other purpose, unless it is an engine-room-monitoring system (with fire-detection capability) installed on a vessel whose construction was contracted for before January 18, 2000; and (g) The system is certified by a Registered Professional Engineer, or by a recognized classification society (under 46 CFR part 8), to comply with paragraphs (a) through (f) of this section.